DITRA-HEAT KIT includes MATT + 240V CABLE + WIFI capable thermostat
- Combine the beauty of tile with the comfort of an electric floor warming system—adding luxury to any room
- The kit contains the DITRA-HEAT uncoupling membrane to prevent tiles from cracking, a heating cable, and DITRA-HEAT-E-WiFi programmable thermostat.
- Customizable heating zones can be created by placing heating cables wherever heat is desired
- Easy to install; no need for clips, fasteners, or self-levelers
- Minimizes assembly thickness for easy transitions to lower surface coverings
- Provides electric floor warming for use beneath tile, stone, or other resilient floor coverings (e.g. LVT)
PRODUCT CODE: DHEKRTW
This kit includes:
sheets DITRA-HEAT membrane
1 spool DITRA-HEAT-E-HK heating cable
1 white programmable Wi-Fi touchscreen thermostat
Voltage: 240 V
IMPORTANT Ordering Information for Schluter®-DITRA-HEAT Cables
- Do not purchase a heating cable that is the same size as the area to be tiled; you will be left with too much heating cable!
- Very important: Never CUT or modify the heating cable in any way. This would change the cable resistance, will cause damage to the cable, and could cause cable overheating.
- A cable spacing of 3 studs is standard.
- The cable may also be spaced at continuously alternating 3 stud – 2 stud intervals in isolated areas or over the entire floor. This practice may be desirable to increase heat output (e.g., over uninsulated on or below grade concrete subfloors) or to consume more cable length in a given area (e.g., when using the standard 3 stud spacing doesn’t allow the selected cable to fit the floor area and respect minimum spacing requirements from walls, partitions, etc.)
- A cable spacing of 4 studs is not recommended, as it can produce inconsistent floor surface temperatures.
- Minimum spacing from walls, partitions, and fixed cabinets is 2" (50 mm).
- Minimum spacing from other heat sources (baseboard heaters, other fixed heating devices, fireplaces, etc.) is 8" (200 mm).
- The minimum spacing from any plumbing drain and forced-air heating duct is 4" (100 mm).
- The minimum spacing from the centerline of toilet drains is 7" (180 mm).
- NEVER install the heating cable under vanities with no air space beneath, bathtub platforms, freestanding bathtubs with no air space beneath, kitchen cabinets and islands, any other fixtures in storage or clothing closets. Excessive heat will build up in these confined spaces and may cause cable overheating.
- NEVER install the heating cable under or through a wall, partition, or floor.
- NEVER install the factory splice (i.e., the black plastic junction between the cold lead and gray heating cable) in the wall. This will cause overheating, system failure, and could cause damage. This splice must be installed entirely under the floor covering, as shown in the heating cable installation instructions.
- It is helpful to plan the location of a buffer zone, as it is not always possible to predict where the heating cable will end. The buffer zone is an area where heating is not essential, typically behind a toilet or adjacent to a door opening. This area allows for the placement of the excess heating cable. Heating cables may also be installed 6" (150 mm) from the wall to create a buffer zone.
- Heating cable testing is required while the heating cable is on the spool and at two subsequent steps during installation to ensure cable quality and for warranty purposes. A megohmmeter is required for the insulation resistance testing of the heating cables. Insulation resistance testing is strongly recommended.
- Consult a qualified electrician before ordering DITRA-HEAT heating cables to ensure you order the correct voltage for your installation.
Payment & Security
Your payment information is processed securely. We do not store credit card details nor have access to your credit card information.